A utilities company in northwest Georgia has trusted Fire Systems with the inspection of their suppression system in their main server room for over a decade. The inspection took one technician and one day. An FM200 system with three tanks was inspected. Each tank had 30 – 40 devices. A smaller system with one tank and 15 – 20 devices was also inspected.